Progress: Addressed, Not Adequately
DOT Relevance: 192.501 192.517
Material testing falls under Subpart J (Test Requirements) of 49 CFR 192. Per the Code, This subpart prescribes minimum leak-test and strength-test requirements for pipelines.
Burst testing is one mechanism to verify design parameters and assumptions.
SRNL recommends that mechanical tests for materials to be used for hydrogen service include burst testing.
Burst testing as a topic is not covered in ASME B31.12. Standards for burst testing of materials and structures to be used for hydrogen pipelines should be established and incorporated by reference into the federal code.